Rozelle Blocked Drain
WHY WE WERE CALLED
We were called to Rozelle after reports of 2x houses side by side experiencing a blocked drain, once onsite the tradesman used CCTV footage (plumbing camera) to investigate the issue to find a partically collapsed sewer line.
WHAT WE DID
The Rozelle plumber noted the line was original earthenware and was a shared party line across two homes, the pipework was cracked & showed signs of completely collapsing if left any longer.
The tradesman was required to excavate to gain better access to the line in order to use a high-pressure jetter to remove the tree roots from the line, once the line was clear of roots and debris the tradesman relined the affected section of earthenware pipework to avoid it completely collasping.